ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
|Published (Last):||20 June 2010|
|PDF File Size:||3.8 Mb|
|ePub File Size:||5.38 Mb|
|Price:||Free* [*Free Regsitration Required]|
Where possible, identify the date a fire detector is changed. Ancillary functions visual indicators operates.
All addressable devices must be individually listed on the Device Test Record sheet.
Sprinklers and spray nozzles protecting commercial cooking equipment and ventilating systems replaced except for bulbtype which show no sign of grease buildup? Plugging of sprinklers found during activation or alteration? Manual transfer from alert signal to alarm signal. For homeowners with ten year old multi-station type smoke alarms or who ulv be contemplating changing or upgrading their existing units!
The communicator has been placed back into dan. Hose connection pressure reducing valves partial flow test. P Emergency telephone operable or in-use tone at handset operates. Smoke and fire detectors should be considered an integral part of any home or business security system. System is returned to service after an extended period of non-service?
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Description of ancillary equipment controlled by the fire alarm system. Ulf for ancillary functions operate as per design and specification. Alarm valve free from damage, trim in correct position, and no leakage? Reconnect ancillary functions off site connections? There are two types of smoke detectors alarms: Test batteries for specific gravity and state of charge?
If any of the following were discovered, was an obstruction investigation conducted and the system flushed? Yes No Oil Pressure: Fire shutter release activated by fire alarm system? Power ulx ancillary devices is taken from the control unit or transponder that is designed to provide such power.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Cap in place and not damaged? Modern smoke alarms will only switch low voltage i.
J Correct electrolyte level. Special Inspection Postal Code: Common trouble signal operates.
Standards Council of Canada
A B C Confirm that a trouble signal is received at the control unit or transponder under an open loop fault. Confirmation of wiring supervision and ground fault indication is required to be carried out at all end-of-line devices on an annual basis. Outlet hose threads are undamaged?
Fire Alarm System Inspection S36. V Visual indicator test lamp test operates. Monthly Inspection and Tests A Pilot lights are functioning? Sequence of operation confirmed and tested. Pressure control valve passed test?