Find great deals for Gamewell Flex If LCD Display With CPU Fire Alarm Board ASSY If Shop with confidence on eBay!. The Gamewell Retrofit Kits offered by Gamewell-FCI provide a simple way to convert without replacing the existing Gamewell backbox. IF panel. Gamewell IdentiFlex Fire Alarm Control Panel. FIRE ALARM AND SMOKE DETECTION SYSTEM. 1. GENERAL. RELATED DOCUMENTS.
|Published (Last):||25 October 2011|
|PDF File Size:||17.75 Mb|
|ePub File Size:||6.47 Mb|
|Price:||Free* [*Free Regsitration Required]|
Previous topic Next topic.
• View topic – Gamewell IF heat detector false alarms
There are 2 different addressable loop cards available for it. Recently, UL updated it’s fire alarm standards from 8th edition to 9th edition. I’ve replaced the detector and now the base, but the issues continue. Would anyone happen to know if just like with the Notifier systems, that system points in the IF may just go bad??? January 13, Gamewell IF heat detector false alarms. Now there is ventilation provided by an exhaust fan and two open-air elctro-mechanical dampers, all of which are open and running.
It is a Gamewell System model IF January 16, You get the picture. Further, the rate of rise is consistent with the second tower on the property, which is not having this issue. With care and maintanence, commercial grade smokes last a long time, but a facility like a school is a pretty hard use environment.
Mon Sep 22, 5: This card is made to run the older Gamewell Apollo XP95 devices.
Gamewell FCI IF610 Manuals
I am also being told that all of our detectors need to be replaced as they are almost id610 years old and past their life expectancy. The location is inside the elevator machine room on the roof top of a 10 story tower in Long Beach. You can’t win; you cant’ break even; and you can’t get out of the Game. The company I work for has been with Gamewell for over 40 years.
Tue Sep 23, We have literally hundreds of customers that have older gamewell systems in them. This way the customer has a system that is new and up to code as well as being able to purchase the apollo devices when needed.
SMF – Just Installed! Now a few years later the system gets swapped out with an E3 system and all of a sudden there is an extra address trouble on the panel. There are replacement parts available though. Hello everyone, I’ve exhausted all of my outside resources now troubleshooting the cause of false alarms from a XPT addressable heat detector on an IF system.
You do not have the required permissions to view the files attached to this post. I don’t know if they’re still in business as the company making the city master fire alarm boxes but the fire alarm panel line became Gamewell-FCi and then got swallowed up into the Honeywell cluster. That said There is a new read 2 to 3 years old panel out that you may want to look into. The E3 can be a direct replacement for the 6oo series GW panels. This works great too.
Make sure the heat detectors are rated for the same environment. IF that is the case, then would anyone happen to have the software that I need to change the device address and the related functions in the program?? That being said, what temperature rating sprinklers are installed? Either way I would look into the E3 as a solution for the Gamewell Gamewell has been around forever, I’ve seen some really old systems by them that are probably obsolete.
They gaewell under the Honeywell umbrella. Anyone who tells you all their jobs are perfect is full of SH1t. You cannot post new topics in this forum You cannot reply to topics in this forum You cannot edit your posts in this forum You cannot delete your posts in this forum You cannot post attachments in this forum. Wed Sep 24, 6: